6,000 SF new choir wing addition and renovation to adjacent 3,000
meeting room and support space.
Two (2) 5 ton split systems with DX cooling coil with constant
volume supply fans. Two (2) oil-fired
hot air furnaces for heating. 500-gallon buried double wall oil
tank with leak detection. Exhaust fan on the
existing flat roof to exhaust toilet rooms, basement and kitchen.
Ventilation air required by code provided
by operable windows.
100-amp circuit breaker and feeder from existing 400-amp
main distribution. Decorative lighting and
controls, battery powered emergency lighting. Occupancy sensor
control of toilet rooms lighting.
Expansion of existing fire alarm/burglar system.
Water main will be extended in the new basement and crawl space
to feed new plumbing fixtures and
domestic water heater. 40-gallon electric hot water heater located
in the new basement. A 4"
sanitary main shall collect all new and existing plumbing fixtures
and reconnect to existing
4" main feeding existing septic field.